Open as PDF
As for outdoor unit circuit, please see Installation Manual of outdoor unit.
Note: All electric wires have their own poles, poles must match that on terminal block.
9. INSTALLATION OF ORNAMENT PANEL
1. Prepare ornament panel Handling of ornament panel
Ornament panel shall not be placed face down or against wall, neither
on an uneven object.
Don' t bend carelessly the swing flap, or, problem may occur.
Remove air inlet grill from ornament panel *
Push in the bar on inlet grill and lift it up. (Refer to Fig. 1)
Lift it up for about 45 degree and remove it from ornament. Tear off adhesive
tape fixing air filter on the back of the air inlet grill. (Refer to Fig. 2)
Be sure to show customers Operation Manual and guide them how to operate unit
correctly. Before installation. read also the Installation Manual of indoor unit.
With this ornament , 2 or 3 air flow direction is not available.
Suitable height is 3 m.
Remove cover plate at corner
Tear off the adhesive tape, and slide it off. (Refer to Fig. 3)
8. WIRING EXAMPLE
Cautions for the installation
All supplied parts. materials and wiring operation must in appliance with
local code and regulations.
Use copper wire only.
When make wiring, please refer to wiring diagram also.
All wiring work must be done by qualified electricians.
A circuit breaker must be installed, which can cut power supply to all system.
See Installation Manual of outdoor unit for specifications of wires, circuit breaker, switches and wiring etc.
Connecting of unit
Remove cover of switch box (1) , drag wires into rubber tube A, then, after proper wiring with other wires,
tighten clamp A. Connect wires of correct pole to the terminal block inside.
Wind seal 12 around wires. (Be sure to do that, or, dew may occur).
Upon connecting, replace control box cover (1) and (2).
Obscrve the following when connecting power supply
Don't connect wires of different specifications to the same
(Loose wire may cause overheating of circuit)
Connect wires of same specifications as shown in right Fig.
Connect wires of the
at two sides.
Don't connect wires of
the same specifications
at one side.
Don't connect wires
of the different
Cover of control box(1)
Rubber tube A
Cover of control box(2)
Attach seal pad
Don't fail to seal it, or water may come in.
Note: Have it sealed, leaving no space.
Seal pad (small size )
(Wind around wire)