Open as PDF
Check whether indoor unit is horizontal with leveler or polythene pipe filled with water , and check
that the dimension of the ceiling opening is correct. Take off the lever gauge before install the ornament
Fasten the screws to make the height difference between the two sides of indoor unit less than 5mm.
First fix it with screws temporally.
Fasten the two temporally fixing screws
and other two, and tighten the four screws.
Connect the wires of synchro-motor.
Connect the wire of signal.
If no response of remote controller,
check whether the wiring is correct,
restart remote controller 10 seconds
after shut off power supply.
<Limits of panel board installation>
Install the panel board in the direction shown in the figure.
The incorrect direction will result in water leakage,
meanwhile swing and signal receiving are displayed that
cannot be connected.
(For series 182 )
POWER SUPPLY: 1PH,220-230V~,50Hz
1 2 3 L N
1 2 3
Electric control box