Open as PDF
2. If the supply cord is damaged, it must be replaced by the manufacturer or its
service agent or a similar qualified person. An extend cord is not recommended,
the requirement of the power supply cord is H07RN-F 3G 2.5mm
installation in European region)
3. If the fuse on PC board is broken please change it with the type of T3.15A /250VAC.
4. The waste battery shall be disposed properly.
5. The wiring method should be in line with the local wiring standard.
6. Use copper wire only. The connecting cable should be H05RN-F 4G 0.75mm
The power cable should be H07RN-F 3G 2.5mm
. All the cables shall have got the
European allthentication certificate.
7. The power supply connects from the outdoor side.
8. The breaker of the air conditioner should be all-pole switch; and the distance
between its two contacts should be no less 3mm.
9. The indoor unit installation height is at least 2.5m.
1. Applicable ambient temperature range:
The machine is adaptive in following situation
Part of the power supply of the air conditioner are not prepared because of the
requirement of the dealer, the power supply should be provided for oneself.
D.B / W.B
D.B / W.
43 C/ 26 C
D.B / W.B24 C/ 18 C
18 C/ 14 C
32 C/ 23 C
D.B / W.B-7 C/ -8 C