Special offers from our partners!
Click here to find your replacement light bulbs at Bulbamerica.com
Open as PDF
Printed in U.S.A.
FAILURE TO READ AND FOLLOW ALL INSTRUCTIONS CAREFULLY
BEFORE INSTALLING OR OPERATING THIS CONTROL COULD CAUSE
PERSONAL INJURY AND/OR PROPERTY DAMAGE.
EMERSON ELECTRIC CO.
9797 REAVIS ROAD
ST. LOUIS, MISSOURI 63123-5398
Non-Programmable Electronic Digital
Heat Pump Thermostat
PART NO. 37-5741A
Operator: Save these instructions for future use!
20 to 30 VAC 50/60 Hz. or D.C.
0.05 to 1.5 Amps (Load per terminal)
1.5 Amps Maximum Total Load (All terminals
Setpoint Temperature Range:
45°F to 90°F (7°C to 32°C)
Operating Ambient Temperature Range:
32°F to 105°F
Operating Humidity Range:
0 to 90% RH (non-condensing)
Shipping Temperature Range:
-40°F to 150°F
For use with:
• Heat pump systems with up to two stages heat,
one stage cool
DO NOT USE WITH:
• Millivolt systems
• Systems exceeding 30 VAC and 1.5 amps
• 3-wire zoned hydronic heating systems
Your new White-Rodgers Digital Heat Pump Thermostat
uses the technology of a solid-state microcomputer to
provide precise temperature control. This thermostat of-
fers you the flexibility to set heating and cooling tempera-
tures that fit your needs.
• Simultaneous heat and cool temperature storage
• LCD continuously displays set point and room tem-
• °F/°C convertibility
• Temperature range 45° to 90°F
• Eight terminals for single or two-transformer systems
• O/B terminal for heat pump systems
• Armchair Demonstration Capability
To prevent electrical shock and/or equipment
damage disconnect electric power to system at
main fuse or circuit breaker box until installation
Do not use on circuits exceeding specified volt-
age. Higher voltage will damage control and
could cause shock or fire hazard.
Do not short out terminals on gas valve or pri-
mary control to test. Short or incorrect wiring will
damage thermostat and could cause personal
injury and/or property damage.
This thermostat is intended for use with a 24-volt system;
do not use this thermostat with a millivolt or line voltage
system. If in doubt about whether your wiring is millivolt,
line, or low voltage, have it inspected by a qualified
heating and air conditioning contractor or electrician.
Do not exceed the specification ratings.
All wiring must conform to local and national electrical
codes and ordinances.
This control is a precision instrument, and should be
handled carefully. Rough handling or distorting compo-
nents could cause the control to malfunction.