Special offers from our partners!
Shop Thermostats & Home Security at Crutchfield today!
Open as PDF
must not bend
2,300mm or more
Maximum pipe length 15m
Minimum pipe length 5m
above 50mm when
installed on the
ceiling of balcony
give clearance as
wide as possible
SPLIT UNIT AIR CONDITIONER
Indoor Unit Outdoor Unit
ø 65mm Power Drill
Key ( 4mm)
Wrench (14, 17, 22mm)
Carefully read through the procedures of proper
installation before starting installation work.
The sales agent should inform customers regarding
the correct operation of installation.
Tools Needed For Installation Work
Read the safety precautions carefully before operating the unit.
The contents of this section are vital to ensure safety. Please pay special attention to the following sign.
WARNING ........ Incorrect methods of installation may cause death or serious injury.
CAUTION ......... Improper installation may result in serious consequence.
Be sure that the unit operates in proper condition after installation. Explain to customer the proper way of operating
the unit as described in the user’s guide.
A circuit breaker or fuse must be installed. Without a circuit breaker or fuse the danger of electric shock exists.
A main switch with a contact gap of more than 3mm has to be installed in the power supply line to the outdoor unit.
Do not install the unit near a location where there is flammable gas. The outdoor unit may
catch fire if flammable gas leaks around it.
Please ensure smooth flow of water when installing the drain hose.
Piping shall be suitable supported with a maximum spacing of 1m between the supports.
Please request your sales agent or qualified technician to install your unit. Water leakage, short circuit or fire may occur if you
do the installation work yourself.
Please observe the instructions stated in the installation manual during the process of installation. Improper installation may
cause water leakage, electric shock and fire.
Make sure that the units are mounted at locations which are able to provide full support to the weight of the units. If not, the
units may collapse and impose danger.
Observe the rules and regulations of the electrical installation and the methods described in the installation manual when
dealing with the electrical work. Use power cables approved by the authorities of your country.
Be sure to use the specified wire for connecting the indoor and outdoor units. Please ensure that the connections are tight
after the conductors of the wire are inserted into the terminals. Improper insertion and loose contact may cause over-heating
Please use the specified components for installation work. Otherwise, the units may collapse or water leakage, electric shock
and fire may occur.
Be sure to use the specified piping set for R410A. Otherwise, this may result in broken copper pipes or faults.
When installing or removing an air conditioner, do not allow air or moisture to remain in the refrigeration cycle. Otherwise,
pressure in the refrigeration cycle may become abnormally high so that a rupture may be caused.
Be sure to ventilate fully if a refrigerant gas leak while at work. If the refrigerant gas comes into contact with fire, a poisonous
gas may occur.
After completion of installation work, check to make sure that there is no refrigeration gas leakage. If the refrigerant gas leaks
into the room, coming into contact with fire in the fan-driven heater, space heater, etc., a poisonous gas may occur.
Unauthorized modifications to the air conditioner may be dangerous. If a breakdown occurs please call a qualified air conditioner
technician or electrician. Improper repairs may result in water leakage, electric shock and fire, etc.
FOR SERVICE PERSONNEL ONLY
THE CHOICE OF MOUNTING SITE (Please note the following matters and obtain permission from customer before installation).
The unit should be mounted at stable, non-vibratory location which
can provide full support to the unit.
The Outdoor unit must be mounted at a location which can sup-
port heavy weight. Otherwise, noise and vibration will increase.
No nearby heat source and no obstruction near the air outlet is
The clearance distances from top, right and left are specified in
The location must be convenient for water drainage and pipe
connection with the Outdoor unit.
To avoid interference from noise please place the unit and its
remote controller at least 1m from the radio, television and inverter
type fluorescent lamp.
To avoid any error in signal transmission from the remote controller,
please put the controller far away from high-frequency machines
and high-power wireless systems.
The installation height of indoor unit must be 2.3m or more in a
non public area.
Do not expose the unit under direct sunshine or rain. Besides, ventilation
must be good and clear of obstruction.
The air blown out of the unit should not point directly to animals or plants.
The clearances of the unit from top, left, right and front are specified in
figure below. At least 3 of the above sides must be open air.
Be sure that the hot air blown out of the unit and noise do not disturb the
Do not install at a location where there is flammable gas, steam, oil and
The location must be convenient for water drainage.
Place the Outdoor unit and its connecting cord at least 1m away from the
antenna or signal line of television, radio or telephone. This is to avoid
Do not install outdoor unit facing strong wind direction. It may damage the
Names of Indoor Components
The Length of Indoor Unit
Figure showing the Installation
of Indoor and Outdoor Unit.
Screw for holder of
AAA Size Battery
Direction of Piping
Dimension of Mounting Stand
of the Outdoor unit
(unit : mm)
Holder for Remote
There are 4 directions
allowed, namely, horizontally
perpendicular to the unit,
vertically down from right,
horizontally out from right and
horizontally out to left.
Don’t form the piping
downward at the left of the unit.
● The difference in height
between the indoor and
outdoor unit should be
kept max 5m.
● The connecting pipe, no
matter big or small,
should all be insulated
with insulation pipe and
then wrapped with vinyl
tape. (The insulator will
deteriorate if it is not
wrapped with tape).
The connection of insulated
Please use insulated drain
hose for the indoor piping
The indoor piping should be
insulated with the enclosed
insulation pipe. (If the
insulator is insufficient,
please use commersial
inner diameter ø 16mm
Be sure to
Screw for Hanger
Names of Outdoor Components
to the unit
The installation height
of indoor unit must be
2.3m or more in a non
Installation of Hanger, Wall Penetration and Installation of Protection Pipe
The draining of the water container inside the indoor unit can be done from the left.
Therefore the hanger must be fixed horizontally or slightly tilted towards the side of
drain hose. Otherwise, condensed water may overflow the water container.
Direct Mounting On The Wall
Please use hidden beams in the wall to hold the hanger.
Wall Penetration and Installation of Protection Pipe
Drill a ø 65mm hole on
wall which is slightly tilted
towards the outdoor side.
Drill the wall at a small
Cut the protection pipe
according to the wall
Empty gap in the sleeve
of protection pipe should
be completely sealed
with putty to avoid
dripping of rain water into
Procedures of Installation and Precautions
Procedures to fix the hanger.
1.Drill holes on wall. 2. Push plug into the holes. 3. Fix the hanger on wall
(As shown below) (As shown below) with 4.1 x 32 screw
(As shown in figure below)
Procedures to fix the holder of remote control.
1.Drill holes on wall. 2. Push plug into the holes.
(As shown below) (As shown below)
Installation of the Indoor Unit
VERTICALLY DOWNWARD PIPING
Connect connecting cord.
Pull out the pipe, connecting cord and drain hose.
The upper part of the Indoor unit is hanged on the hanger.
The projection at the lower part of the Indoor unit is hooked onto the hanger.
Please pull the lower part of
the Indoor unit outwards to
check if the unit is hooked
onto the hanger. Improper
installation may cause
vibration and noise.
Change of Drain Hose and Installation Procedures.
Exchange the location of drain hose and drain cap during horizontal piping as shown in
figure below. Be sure to plug in the drain hose until the insulating material folds upon itself.
Please use pliers to pull out the drain cap.
(This is an easier way to remove the drain cap).
INSTALLATION OF REFRIGERATING PIPES AFTER CONNECTION
The refrigerating pipes should be adjusted to fit into
the hole on the wall and then ready for further
The terminals of 2 connected pipes must be covered
with insulator used for terminal connection. Then the
pipes are wrapped with insulation pipe.
Connect the connecting cord after removing electrical
cover. (Refer to “CONNECTION OF POWER CORD”)
After adjustment, fit the connecting cord and pipes
into the space available under the indoor unit. Use
holder to hold them tight.
The rubber strap used for
fixing the insulator should
not be tied with great force.
Otherwise, this will damage
heat insulation and causes
Holder can be attached at the either of 2 places.
Please select the easier position.
THE CONNECTION OF REFRIGERATING PIPE DURING THE
INSTALLATION OF INDOOR UNIT
Preparation To Install Refrigerating Pipes
Please fix in the plastic core
after flaring to avoid plastic
chips entering the pipes.
You are free to choose the side (left or right) for the installation of drain
hose. Please ensure the smooth flow of condensed water of the Indoor
unit during installation. (Carelessness may result in water leakage.)
Be sure that the
drain hose is not
Be sure that the wire is not
in contact with any metal
in the wall. Please use the
protection pipe as wire
passing through the hollow
part of the wall so as to
prevent the possibility of
damaged by mouse.
Unless it seals completely,
any air with high humidity
flows from outdoor and
any dew may drop.
The refrigerating pipes and connecting cord
transform and are attached.
The end of the refrigerating pipes are at locations
marked with “
Installation of Drain Hose
Hang the Indoor unit onto the hanger. Use the temporary stand
at the back of the Indoor unit to push its lower part 15cm
Place the drain hose through the hole on the wall.
Wrap the refrigerating pipes with insulation pipe after
connecting refrigerating pipe.
Connect the connecting cord after removing electrical cover.
(Refer to “Connection of Power Cord”)
After adjustment, the connecting cord and refrigerating pipes
are placed into the space available under the Indoor unit.
The projection of Indoor unit must hook to the hanger.
4.1 x 32 Screw
HOW TO REMOVE INDOOR UNIT
Push up the (PUSH) sections at the
bottom of the indoor unit and pull the
bottom plate towards you. Then the
claws are released from the stationary
(The (PUSH) sections are indicated by
2 arrows in the right figure)
2 ~ 5mm
Connecting cords, pipe and
drain hose must be laid
together with Vinyl tape.
Lift the body
of the unit
then force it
Condensed water may leak out if not inserted properly.
HORIZONTAL & DOWNWARD PIPING – MAKING OPENINGS
During horizontal or downward piping, use a knife to cut
openings as shown in figure. Then smoothen the edges of
openings with a file.
Turn the piping while holding down the lower
portion of pipe-support by hand.
Drain hoseDrain cap
Pull up the pipe after
Insulation pipe (must be wrapped with
vinyl tape at every 120mm).
Rubber strap tied with great force
Please bend at a small
radius to form an arc
Heat insulation pipe
Pull this to the front
during the connection
of refrigerating pipes
to ease task.
Hole for pipe
Please use more
than 4 screws.
Screw for Hanger