Open as PDF
Part Numbers 33CS2PPRH-01 and 33CS2PP2S-01
Read and follow manufacturer instructions carefully. Fol-
low all local electrical codes during installation. All wiring
must conform to local and national electrical codes. Improper
wiring or installation may damage thermostat.
Recognize safety information. This is the safety alert sym-
bol z_. When the safety alert symbol is present on equipment
or in the instruction manual, be alert to the potential for person-
Understand the signal words DANGER, WARNING, and
CAUTION. These words are used with the safety alert symbol.
DANGER identifies the most serious hazards which will result
in severe personal injury or death. WARNING signifies a haz-
ard which could result in personal injury or death. CAUTION
is used to identify unsafe practices which would result in minor
personal injury or property damage.
The Edge Pro thermostat by Carrier is a wall-mounted, low-
voltage control which combines temperature and humidity
control in either a single or two-piece unit. The Edge Pro ther-
mostat can be set for 7-day, 5/2-day, or 1-day progralrunable
operation. Different heating and cooling set points and thnes
are progralrunable for 2 or 4 periods per day. The thermostat
can also be configured for non-progralmnable operation. When
operating as a non-progralmnable thermostat, the user will still
have both temperature and humidity control.
The Edge Pro thermostat has no need for batteries to store
user-configured settings in memory. During power loss its in-
ternal memory saves settings for unlimited time, and the clock
continues to run for at least 24 hours. An extension of Carrier's
proven line of thermostats, the Edge Pro thermostat provides
separate set points for heating and cooling in addition to hu-
midification and dehumidification.
Thermostat Display -- Thethermostat display is locat-
ed in the center of the thermostat. See Fig. 1. The following
information can be displayed on the screen:
• dayofthe week
• progralmning option (indicates which settings are being
• filter and UV lamp service reminders
• current temperature
• current program routine (follow scheduled program-
ming, hold current settings, or run holiday program)
• fan mode (on, auto)
• current system mode (heating, cooling, emergency heat,
heat/cool (auto), off)
• humidify or dehumidify settings
• Fahrenheit or Celsius display
• advanced progralmning indicators
• keypad locked or unlocked
• programming option (indicates which settings are being
• system is in auxiliary (supplemental) mode
• cooling set point
• heating set point
• holiday schedule return date
• length of time for temporary temperature hold (ovemde)
• outdoor temperature
• leaving air temperature
• time period start
• period of the day
Thermostat Front Panel Buttons-- The thermo-
stat has buttons under the front cover which are used for vari-
ous functions such as raising or lowering the desired set point
and changing the current mode. See Fig. 2.
SET BUTTON -- This button enters the thermostat program-
ming schedule and allows the user to adjust the clock and
change the calendar.
SCHEDULE BUTTON- This button allows the user to
choose to follow a schedule, hold the current set points, or go
into holiday mode.
OCCUPIED BUTTON- This button temporarily changes
the thermostat from Unoccupied to Occupied settings.
MODE BUTTON -- This button selects whether the thermo-
stat is set for heating, cooling, emergency heat, auto (heat and
cool as needed), or off modes.
DONE BUTTON--This button saves the settings when
completing a setup or progralruning step.
follow schedule _ auto _ off
hold I_ on _ heat
_ ho,iday QQ_ I_ coo,
checkUVlight !_ Em heat
Cl 0 . pressdone
...clock ...calendar ...dailyschedule ...holidaysettings
I_ Mo t O O auxiliary ]
mu outsidetemp heaton
1_ We IP-occ startat returnon heat cool
I1_Th 1_ occ2 temporaryholdfor setat: setat: r
t_Fr _.occ3 AIO. = RR] O! L='IQ
1_ Sa I_unocc _._ _j-_,_J]
I_ Su dehumidify M D heatY on2 coolon L
Fig. 1 -- Thermostat Display
Manufacturer reserves the right to discontinue, or change at any time, specifications or designs without notice and without incurring obligations.
Catalog No. 04-53330011-01 Printed in U.S.A. Form 33CS-20SO Pg 1 7-08 Replaces: New